Click on the >_ symbol to go to the commands section.
Sync parameters: Forces a synchronisation of the device parameters with priority given to the data stored in the device
Notifications allow you to establish a mechanism to alert users when certain types of alarms occur. The notification rules determine which alarms generate a notification, as well as to whom these notifications are sent. Notifications can be sent via email.
Shows the list of configuration changes.
Origin: Indicates the origin of the parameter change:
Parameter: Indicates which parameter has been changed.
Previous / Current: Indicates the parameter value before and after the change.
User: Indicates which user made the change.
Date: Indicates the date and time of the change.
Displays the list of events and alarms recorded by the device
Reference: Indicates the reference of the event/alarm:
Type: Indicates the type of event/alarm.
Status: Indicates whether the event/alarm is active.
Name: Displays the description of the event/alarm.
Severity: Indicates the priority of the event/alarm.
Activated: Indicates the activation value (if applicable).
Activated on: Displays the activation date and time of the event/alarm.
Deactivated: Indicates the deactivation value (if applicable).
Deactivated on: Displays the deactivation date and time of the event/alarm.
Ack user: Indicates which user acknowledged the alarm.
ACK date: Indicates the date the alarm was acknowledged.
Allows you to change the configuration of the device and AKONET.cloud (alarms, set points, etc.). For more information, see the configuration section of each device.
There are two types of parameters:
Changes to the parameters associated with the device generate a task that runs during the next transmission (variable depending on configuration); refer to the device manual to force the transmission.
Changes to the parameters associated with AKONET.cloud have immediate effect.
If, upon altering a parameter, there is a pending task, the change is added to that task, otherwise it generates a new task. The list of tasks and their status can be found in the backlog section .
Allows saving or uploading configurations used frequently by facilitating the parametrisation of the devices.
To save a configuration, once the parameters have been set as required, click on "Presets" and then "Save as". A window opens for assigning the configuration name and description.
To upload a previously saved configuration, click on "Presets" and mark the desired option. A summary of the applicable changes is displayed. Click on “Apply” to save the changes and then click “Save” and “Send configuration”. This creates a new task in the backlog which is run in the next transmission) or “Delete” to delete the selected preset, or “Cancel” to exit without changing anything.
Allows you to set the time periods during which alarms do not generate notifications and are not indicated in the reports, although they are shown in the list of events. For all intents and purposes, any alarm goes into the “Unassigned” status during this period.
1: Activates or disables the schedule notification. If disabled, notifications are always sent. In the example, alarm notifications are only sent on Mondays between 02:15 and 04:30 and on Wednesdays between 8:00 and 10:00.
2: Click on a day to activate notifications on that day and select the start and end times to send alarm notifications.
3: Checking this box enables the calendar that allows you to select which days the device does not send notifications.
4: Click to select / deselect the days on the calendar. The device will not send notification on the selected days.
If this schedule is modified in a device within the “groups” section, the “Apply configuration to all” option appears, which applies the same schedule to all devices in the group, deleting their previous schedule configuration.
Changing the device to be displayed
To change the device to be displayed, click on the indicated button: