The box that summarises the information on each device is referred to as the "Widget".
The device sends the stored data to Akonet.cloud, as well as the alarms and alerts detected according to the configured transmission interval. When received, the widget for the corresponding device flashes for 1 minute indicating correct reception. During this time, the data shown correspond to the real-time measurement. After 1 minute, the operation averages are displayed again.
The striped area shows the full measurement range of the device, while the solid area indicates the range of actual work (maximum and minimum value reached) during the selected time period.
If there is an alarm, the outline flashes red; if the alarm has been confirmed (mute) the outline is turned off.
A flashing red halo means that the alarm(s) has/have not been confirmed
By passing the mouse over the indicator, it displays the date and time of the last synchronisation.
If a NBIoT connection is available, the signal strength is also displayed and the colour indicates the signal quality:
HACCP (Hazard Analysis and Critical Control Points): Indicates whether there has been any HACCP alarm in the ambient or external probe and displays its temperature value.
COOL: Displays the percentage of time that the device has been generating cooling (COOL relay activated) during the selected period.
DEFROST: Displays the percentage of time that the device has been in defrost during the selected period.
Shows the detail of each device as well as a summary of the data captured and allows adjusting the operating parameters.
Hide / Show Details
Shows / hides the device details.
Displays the controller’s real time reading as well as the different indicators and allows for using some functions of the keypad as if you were in front of the device*.
Functions on Live Mode
*The operation of this mode depends on the quality and speed of Internet connection, in certain cases there may be some delay in the data displayed.
Allows selecting the period displayed on the different graphs and also affects the calculation of the averages indicated in the widget shown on the left.
Displays graphs of the data acquired by the device, there are 10 types of graphs:
Continuous: Displays the values acquired continuously together with the alarm and HACCP levels.
Cooling / defrost / door open activity: Displays the total time per day the device has been in each state.
Door / stand-by activity: Graphically displays the door openings and stand-by mode activations (number of times and total time).
Activity: Displays a daily summary of the maximum, minimum and average temperatures, with reference to the set point.
Time in set point: Displays the daily percentage of time the cold room has been in set point, above and below.
TTI Histograma: Breakdown of the different values obtained in percentage of time and their situation with regard to the set point.
HACCP: Displays a summary of the maximum values obtained for each hour and the configured HACCP alarm value.
Alarms: Displays the total time in alarm per day as well as the activation temperature
Activity (Probe 2): Displays a daily summary of the maximum, minimum and average temperatures, with reference to the set point of probe 2.